1. Adjust the temperature of water supply
We will adjust the water supply temperature of the heating when the radiator is debugged, the water supply temperature of the radiator is set between 70 degrees and 80 degrees, when we actually use the radiator, the water supply temperature of the wall-hung furnace is basically adjusted at about 70 degrees, the surface temperature of the radiator can reach about 60 degrees, and the room can reach the set temperature in about 30-40 minutes.
If you need to increase the temperature of the radiator, the heating water supply temperature of the wall-hung furnace can be set to a temperature close to 80 degrees in the position of the wall-hung furnace, the surface temperature of the radiator will increase, the indoor heating speed will be accelerated, and the temperature can reach the time faster, but the return water temperature of the wall-hung furnace is easy to overheat, and the frequency of the wall-hung furnace start and stop will increase.
2. Adjust the temperature of the indoor thermostat
The radiator system is generally on the same floor, only one host thermostat is set up, the indoor temperature is monitored, so as to play an energy-saving role. Adjusting the temperature of the indoor thermostat is also a way to increase the temperature of the radiator, the indoor temperature is increased, the working time of the radiator will be longer, the time for the radiator to dissipate heat at high temperature will be longer, and the indoor temperature will also increase.
Usually the indoor temperature is set at 20 degrees ± 2 degrees, this range can ensure that the indoor is not cold, personnel move freely, there will be no feeling of heat, and the temperature difference with the outdoor is not very large, and the gas cost consumed is relatively low. Of course, the temperature setting is too low is not good, it consumes energy, and it does not achieve the purpose of indoor heating.
3. Adjust the valve of the radiator
Valve control through the radiator is the most direct way to control the temperature of the radiator.
Adjust the water supply valve, the water supply valve above the radiator determines how much hot water enters the radiator to dissipate heat, the flow of the valve is large, the temperature of the radiator will become larger, the heat dissipation will be very high, in the same way, the valve closed The temperature will be lower. At present, the water supply valve of the radiator will be added with a thermostat or temperature probe control valve, and the temperature of the radiator can be adjusted more accurately through the scale and display.
Adjust the return valve, the adjustment of this valve is mainly for the flow control of each radiator, the adjustment of the return valve is related to the water flow rate and flow inside the radiator, so that the flow of each radiator is uniform, to achieve the effect of the radiator heating up at the same time, generally this valve is adjusted by experienced debugging masters, usually the valve is closed, the opening and closing size of the return valve is also related to the temperature of the radiator.
Adjust the exhaust valve, the function of the exhaust valve is to discharge water and exhaust the radiator. Many times the radiator is not hot, the local is not hot, and there is a running water sound inside the radiator, which is because the radiator is mixed with air, and the exhaust of the radiator after the replenishment of water can increase the temperature of the radiator, and the speed of the radiator temperature increase can be accelerated through drainage.
We can complete the method ourselves, but when it comes to water flow regulation, we also need professional masters to deal with it to reduce the uneven water flow leading to uneven radiator heat.
In addition, the radiator of the water circulation is not recommended to be too hot, such as central heating cast iron radiator, the surface temperature of the radiator will cause burns, the installation of radiators at home should also install protective wall panels, now the separate heating, the water supply temperature of the radiator is between 70-80 degrees, the surface temperature of the radiator is only about 50 degrees -60 degrees, will not cause burns to personnel, aesthetics is also improved a lot, the effect can also reach 18 degrees -22 degrees, the general radiator after debugging the temperature, It can be adjusted without adjustment, and it is easier to operate according to special situations according to needs.